For more than 40 years the Osterbrant AB company has designed, produced and delivered the alarm and indicator
unit PILOT B10.
The Alam and indicator unit PILOT B10 is distributed worldwide and more than ten thousand units have been delivered to many different customers in the power generation and distribution, construction, manufacturing industries etc.
Our specialities are producing to specific customer requirements and rapid delivery.
High quality and reasonable prices come as standard.
The Osterbrant AB company is situated in the Jönköping municipality where there are several high tech companies estabished and a local, reputable School of Engineering. Read more
High customer service accessibility.
We will customise each unit to the customer´s specific need.
We will be able to deliver within a few days.
The PILOT B10 alarm and indicator unit is designed for use in
industrial and similar environments.
The PILOT B10 provides alarms and indications units for automatic control and supervision of processes, machinery, power plants, buildings, etc.
The PILOT B10 will require additional protection if installed externally.
The PILOT B10 is not intended for use as burglar alarm, fire alarm, assault alarm, social alarm, camera supervision systems or access control for safety applications.
The PILOT B10 is available in many types and is adaptable to different applications, specified by the customer. All base units have the same dimensions and electrical connection features. Any unit can be exchanged or replaced with other types of units.
The PILOT B10 fulfils the requirements for the European Market (CE).
For any questions, additional information or discussions about personal requirements/specifications -
please contact us:
Mobile/Cell: + 46 70 7528 730
VAT number: SE556655206201
Bank: Svenska Handelsbanken AB, Huskvarna Sweden
The PILOT B10 alarm unit is equipped with a microprocessor, programmed to give the alarm unit its functions.
The unit is protected by a standard polycarbonate DIN-enclosure, 96x96mm.
All indication lamps are provided by LED´s. Each unit has ten LED´s (channel indication lamps) located vertically with a text area on the front panel.
Alarm LED`s are located at the top of the unit to indicate the status of a failure.
There are push buttons for Reset and Test.
Power, failure contacts and summary relay output are connected to a terminal at the rear of the unit.
A mounting clamp is provided for mounting of the unit.
The software included is not affected, disturbed or dependent on date, clock time, calendar year, turn of year or leap year.
In the event of an alarm signal resulting from a closing or opening contact, the summary
relay will be activated after a preprogrammed time delay. The alarm
LED lights up and the corresponding channel lamp flashes simultaneously showing the location of the failure.
After the failure is rectified the alarm remains active until the Reset-button is pressed.
If the failure remains after pressing Reset, the alarm LED darkens, the summary relay is released and the channel LED changes to a steady light.
When the failure disappears the channel indication light darkens.
A functional test is activated by pressing the Test-button. This causes all LED´s to flash and the summary relay to activate. There is an option to exclude the summary relay from the test.
All types of units can be adapted to different needs and a variety of
functions and accessories described in this document or implemented
as specified by the customer.